# What is the meaning of load loss?

Load-loss factor (LLF) is a factor which when multiplied by energy lost at time of peak and the number of load periods will give overall average energy lost. It is calculated as the ratio of the average load loss to the peak load loss.

Also to know is, why iron losses are not considered in short circuit test?

That’s why compare to copper loss, iron loss is very very less and it can be ignored during short circuit test. Iron losses in short circuit test are not absent they are just neglected. Because in the short circuit test the LV winding is short circuited which means high currrent and low voltage in the secondary side.

What is stray load loss in transformer?

Leakage flux in a transformer produces eddy current in the conductors, these eddy current produces losses that is called stray loss of a transformer. These can be reduced by using thin sheets of insulated iron. Is this answer still relevant and up to date? Load loss in Transformer is sum of copper loss and stray loss.

What is the core loss?

Definition of core loss. : energy wasted by hysteresis and eddy currents in a magnetic core (as of an armature or transformer)

## What are the no load losses?

It is the loss in a transformer that is excited at rated voltage and frequency, but without a load connected to the secondary. No-load losses include core loss, dielectric loss, and copper loss in the winding due to exciting current.

## What is meant by copper losses?

Copper loss is the term often given to heat produced by electrical currents in the conductors of transformer windings, or other electrical devices. Copper losses are an undesirable transfer of energy, as are core losses, which result from induced currents in adjacent components.

## What is meant by eddy current loss?

Eddy Current Loss. When an alternating magnetic field is applied to a magnetic material an emf is induced in the material itself according to Faraday’s Law of Electromagnetic induction. These circulating currents are called Eddy Currents. They will occur when the conductor experiences a changing magnetic field.

## What are the no load losses in a transformer?

No-load losses are caused by the magnetizing current needed to energize the core of the transformer, and do not vary according to the loading on the transformer. They are constant and occur 24 hours a day, 365 days a year, regardless of the load, hence the term no-load losses.

## What is eddy current and hysteresis losses?

Eddy Current Losses: An eddy current is an electric current set up by an alternating magnetic field. These losses arise from the fact that the core itself is composed of conducting material, so that the voltage induced in it by the varying flux produces circulating currents in the material.

## What is meant by hysteresis loss?

The energy lost as heat, which is known as the hysteresis loss, in reversing the magnetization of the material is proportional to the area of the hysteresis loop. Therefore, cores of transformers are made of materials with narrow hysteresis loops so that little energy will be wasted in the form of heat.

## What is meant by iron losses?

Eddy current loss and hysteresis loss depend upon the magnetic properties of the material used for the construction of core. Hence these losses are also known as core losses or iron losses. Hysteresis loss in transformer: Hysteresis loss is due to reversal of magnetization in the transformer core.

## How can we reduce eddy current loss?

In order to reduce the eddy current loss, the resistance of the core should be increased. In other words, low reluctance should be retained. In devices like transformers, the core is made up of laminations of iron. ie,the core is made up of thin sheets of steel, each lamination being insulated from others.

## How can the core losses be minimized?

Core losses majorly include Hysteresis loss and eddy current loss. Eddy Current loss can be reduced by increasing the number of laminations. The laminations provide small gaps between the plates. As it is easier for magnetic flux to flow through iron than air or oil, stray flux that can cause core losses is minimized.

## What is the loss factor?

Loss factor is defined as the percentage difference between rentable area — the number of square feet that office tenants pay for — and usable area. A building with a rentable area of 400,000 square feet and a usable area of 300,000 square feet, for example, has a loss factor of 25 percent.

## How do you calculate loss factor?

The loss factor is calculated by dividing the difference between the rentable and usable square footages by the rentable number. For example, if a space is being called 5,000 sf and the usable square footage is 4,000 sf, the loss factor would be (5,000-4,000=1,000/5,000=) 20%.

## How can we reduce the copper losses in a transformer?

The windings of the transformer are made thick so that the resistances are minimised.Another technique is Vaccum Pressure Impregnation(VPI). In this technique the transformer is kept in vaccum then high pressure varnish is passed so that the smallest of the air gaps are also filled. Hence reducing the copper losses.

## What is the function of no load current in a transformer?

At no load, secondary current becomes zero due to open circuited at secondary. Therefore, only shunt branch component is left which is used to magnetise the transformer coils. The current flowing in coils leads to winding losses. No load current is the current which is used by the transformer to magnetize it’s core.

## Why the rating of transformer is in KVA?

Copper losses ( I²R)depends on Current which passing through transformer winding while Iron Losses or Core Losses or Insulation Losses depends on Voltage. So the Cu Losses depend on the rating current of the load so the load type will determine the powerfactor P.F ,Thats why the rating of Transformer in kVA,Not in kW.

## How efficient is a transformer?

Just like any other electrical machine, efficiency of a transformer can be defined as the output power divided by the input power. That is efficiency = output / input . Transformers are the most highly efficient electrical devices. Most of the transformers have full load efficiency between 95% to 98.5% .

## What are iron losses in a transformer?

An ideal transformer would have no losses, and would therefore be 100% efficient. In practice energy is dissipated due both to the resistance of the windings (known as copper loss), and to magnetic effects primarily attributable to the core (known as iron loss).

## What do you mean by efficiency of a transformer?

Just like any other electrical machine, efficiency of a transformer can be defined as the output power divided by the input power. That is efficiency = output / input . Transformers are the most highly efficient electrical devices. Most of the transformers have full load efficiency between 95% to 98.5%

## What is the function of current transformer and potential transformer?

P.T may be considered as a parallel transformer. The primary current of a P.T depends upon the secondary circuit conditions (burden). The primary winding P.T is connected across the line of voltage to be measured. With the help of P.T, a 120V voltmeter can be used to measure very high voltages like 11KV.

## Why current transformer is used?

A current transformer (CT) is a type of transformer that is used to measure alternating current (AC). It produces a current in its secondary which is proportional to the current in its primary. Current transformers, along with voltage or potential transformers, are instrument transformers.

## Why secondary of current transformer is short circuited?

Secondary Current: Voltage across Ammeter: For this reason a current transformer should never be left open-circuited or operated with no-load attached when the main primary current is flowing through it just as a voltage transformer should never operate into a short circuit.

Categories FAQ